- Size Boiler / Heat Pump
- Request a quote
Dewar Plumbers Dublin replaced and upgraded a customer’s leaking heat pump with the Viessmann Vitocal 200-A 13kW (COP of 4.72 A7/W35) heat pump combined with Vitocell 300-B 300l A-rated cylinder (standby heat loss of 1.06kW/24hr). In order to achieve the minimum volume requirement to allow the heat pump to perform its defrost cycle and to prevent it from cycling a Vitocell 100-E 46l wall hung buffer was used. A low loss header was used with a secondary pump, two motorised valves, and two-room stats to allow for separate control to the ground floor and first-floor heating zones.
We provided the installer with a full system design schematic for both the underfloor heating and heat pump. By doing this it made the installation and commissioning of this project simple and trouble-free. Precision Heating commissioned the installation, and both the client and installer were delighted with the end product.
Client: Dewar Plumbers Dublin
Location: Blackrock, Co Dublin
Completed date: 25/03/2021
Category: Domestic, Heat Pumps, Underfloor Heating